TPYC Shipboard Medium Voltage Power Cable
FA-TPYC Shipboard Medium Voltage Power Cable application：
This Cable can be applied in Marine&Offshore and various ships, ship repair and oil platforms and other offshore buildings control device and general electric lighting,machinery and equipment of factories and mines are also equally applicable.
A-TPYC Shipboard Medium Voltage Power Cable standards ：
IEC 60332-3 Cat.A(for FA-type)
3.6/6KV SPYCB,(FA-) SPYCB,TPYC,(FA-) TPYC
6/10KV SPYCB,(FA-) SPYCB,TPYC,(FA-) TPYC
8.7/15KV SPYCB,(FA-) SPYCBY,TPYC,(FA-) TPYC
FA-TPYCY Shipboard Medium Voltage Power Cable：
|Conductor||T(S)||Tinned annealed stranded copper, class 2 according to IEC 60228|
|Conductor screen||Semi-conducting compound|
|Insulation||P||85°C EPR as per IEC 60092-351|
|Insulation screen||Semi-conducting compound /Tinned copper tape|
|Filler||Non-hygroscopic material (If necessary)|
Galvanized steel wire braid(-C TYPE) or
copper alloy wire braid(-CB TYPE)
|Core identification||3C Red, Yellow, Blue|
|Outer sheath color||Red|
Minimum cable bending radius
The internal radius of cable bends which are not subjected to movements by expansion, is not to be less than :
6 times the external diameter of cable
Cable which are subjected to movements by expansion and the high voltage cable are to be bent to a form of at least 12 times cable diameter.
Minimum recommended temperature of installations :
-10°C Ship wiring cable with PVC sheath
-20°C Elastomeric on/off shore cables
Installations pulling force
The cable pulling force can be estimated, as a maximum limit :5Kp per mm2 conductor area in the cable.Additional tension will be supplied from the braid and the insulation and sheathing compound.
We will provide you with the best quality, competitive prices and satisfactory service.
For more enquiries ,please contact us.
Inquiry/Feedback to our sales office
The easy and safe way to contact us