JIS C3410 Medium Voltage Power Cable
JIS C3410 Medium Voltage power cable application:
This Cable can be applied in Marine and Offshore and various ships, ship repair and oil platforms and other offshore buildings control device and general electric lighting,machinery and equipment of factories and mines are also equally applicable.
JIS C3410 Medium Voltage power cable standards:
– Design guide : JIS C 3410(1999/2010)
– Flame retardant : IEC 60332-1 & IEC 60332-3 Category A (FA-Type)
– Cold bend/impact : CSA 22.2 No. 03 (-35 ) (Cold Type)
– Max. conductor temperature : 85℃
JISC 3410 LV power cable Model:
JIS C3410 Medium Voltage power cable construction:
|Conductor||T(S)||Tinned annealed stranded copper, class 2 according to IEC 60228|
|Conductor screen||Semi-conducting compound|
|Insulation||P||85°C EPR as per IEC 60092-351|
|Insulation screen||Semi-conducting compound /Tinned copper tape|
|Filler||Non-hygroscopic material (If necessary)|
Galvanized steel wire braid(-C TYPE) or
copper alloy wire braid(-CB TYPE)
|Sheath||Y||PVC ST2 type|
|Core identification||3C Red, Yellow, Blue|
|Outer sheath color||Red|
Minimum cable bending radius
The internal radius of cable bends which are not subjected to movements by expansion, is not to be less than :
6 times the external diameter of cable
Cable which are subjected to movements by expansion and the high voltage cable are to be bent to a form of at least 12 times cable diameter.
Minimum recommended temperature of installations :
-10°C Ship wiring cable with PVC sheath
-20°C Elastomeric on/off shore cables
Installations pulling force
The cable pulling force can be estimated, as a maximum limit :5Kp per mm2 conductor area in the cable.Additional tension will be supplied from the braid and the insulation
and sheathing compound.
We will prodvide you with the best quality, competitive prices and satisfactory service.
Inquiry/Feedback to our sales office
The easy and safe way to contact us